The diesel engine operates when the oil is insufficient
D88尊龙At this time, due to insufficient oil supply, the friction surface of each pair of friction pairs is insufficient, resulting in abnormal wear or burn. To this end, the diesel generator must ensure sufficient oil before starting and during the operation of the diesel engine, so as to prevent the failure of cylinder and tile burning due to lack of oil.
Error operation two
Stop immediately after loading or abruptly discharging load.
D88尊龙After the diesel generator is extinguished, the cooling system water circulation stops, the heat dissipation capacity is drastically reduced, the heating parts are lost and the parts of the cylinder head, cylinder liner and cylinder body are overheated, and the cracks are produced, or the excess expansion card of the piston is killed in the cylinder sleeve. On the other hand, the diesel generator will not be cooled by the idle speed during the shutdown, which will make the friction surface oil deficient. When the diesel engine starts to start again, it will aggravate the wear because of the bad lubrication. Therefore, the diesel generator should be dismounted before the fire is extinguished, and gradually reduce the rotational speed and run for several minutes without load. (it requires no load running for 3 minutes).
D88尊龙Error operation three
After the cold start, the non warmer is loaded with load
When the diesel generator is started, the engine oil pump is poor in oil supply due to the poor oil viscosity and poor fluidity, and the machine friction surface is badly worn because of poor oil lubrication. Therefore, the diesel engine should be heated at idle speed after cooling, and the engine oil temperature is above 40 degrees centigrade (when used in winter, when the cooling water reaches 60 degrees C) and then with load operation; the machine should start with low speed gear and run a period of mileage in every position in sequence until oil Wen Zhengchang, oil supply is full, then it can be turned into positive. Drive often.
Error operation four
D88尊龙Heavy throttle of diesel engine after cold start
If the throttle is struck fiercely, the speed of the diesel generator will increase sharply, which will cause some friction surfaces on the machine to wear violently due to dry friction. In addition, the piston, connecting rod and crankshaft receiving force change greatly during the throttle, causing violent impact and easily damaging the machine parts.
Error operation five
Run under insufficient cooling water or high temperature of cooling water and oil.
The insufficient cooling water of diesel generators will reduce the cooling effect. The diesel engine overheat because of the lack of effective cooling; the high temperature of the cooling water and oil will also cause the diesel engine to overheat. At this time, the main heat load of the cylinder head, cylinder sleeve, piston assembly and valve of the diesel generator, such as the mechanical properties such as strength and toughness declined sharply, increased the deformation of the parts, reduced the clearance between parts and accelerated the wear of the machine parts, and also caused the failure of the cracks and the jammed parts of the machine parts. The overheating of the diesel generator will also deteriorate the combustion process of the diesel engine, resulting in abnormal operation of the injector, poor atomization and increased carbon deposition.