1. The engine room of the gas generator set should be far away from the open fire area.
D88尊龙2, gas generator room should be bright and spacious, require the installation of ventilator to ensure good ventilation;
D88尊龙3. When the gas generating set is installed, the base plate and the foundation are leveled with the flat iron. The contact area should be more than 60%, and the distribution is uniform.
4, indoor installation of lighting, switches, lines and electrical appliances should be used explosion-proof measures, and fixed firmly;
5. The engine room of the gas generator set should meet the requirements of fire fighting and equipped with fire extinguisher and other fire-fighting instruments.
6. A combustible gas alarm device is installed in the engine room of a gas generator set, which can be found in time when combustible gas is leaked.
7. The inner diameter of the main pipe of the gas line of a single gas engine under 60kW should not be less than 2 inches, and the inner diameter of the engine near the engine should not be less than 1 inches. The gas generating units above 60kW are 3 and two inches, respectively. And must install gas valve (stainless steel ball valve), type water release valve, anti tempering device, gas pipeline welding finish should clean welding slag (with high pressure air);
D88尊龙8, gas desulfurization, dehydration, to dust, including the flow of hydrogen is less than or equal to 0.25Nm3, less than 10%.